The panel is a GE TLM1612C, ns think.
You are watching: Will eaton breakers fit in a ge panel
TLDR: They"re all wrong. Swap through a GE or divide breaker (e.g. Eaton CL not BR).
You deserve to use several breakers within a panel.Breaker species which are provided on the panel"s labeling, these will be do by the very same manufacturer and the exact same type, and also UL-listed. Breaker species which are contemporary to your panel"s labeling, yet again room still the exact same manufacturer, and they state they will work-related in your panel, or substitute for breakers which space labeled for use in her panel. Also UL-listed. Breakers which space made by a third party, who sends them to Underwriter"s Laboratories to have them UL-listed because that the competitor panel. UL phone call this a "UL-Classified" breaker, and also they operation the same set of tests they operation on manufacturing facility breakers. If you research study the manufacturer the the breaker and their classified breaker lines, lock should present a cross-reference graph stating which manufacturing facility breakers their Classified breakers can substitute for.
Classified is UL"s method of speak these are not OEM breakers and do not have the benefit of the OE"s expertise and also trade-secret knowledge, yet they do pass security testing.
Keep in mind the a manufacturer"s Classified breakers are various breakers than the OEM breakers they make for their very own panels. For instance, Siemens QD breakers room classified because that Square D QO panels, and have to not be offered in any type of Siemens panel of any type of kind.
Similarly, girlfriend will view that Eaton"s CL heat of breakers is no UL-classified for usage in Eaton BR panels -- also though the breakers might look outwardly the same.
This need to not be confused with cross-listing. For instance, Challenger panels have breakers recognized to be defective (but panels are fine). Human being seeking to replace those breakers discover their panel labeling requires type C breakers. They room pleased to uncover that Eaton"s BR line is cross-listed as type BR and type C.
On her panel, we have the right to strike out the Square D breakers immediately. Square D is absolutely opposed to "Classified" breakers. Lock refuse to make classified breakers for competitor panels, and also they object to the usage of share breakers in their panels (not the they have anything come say about it). For this reason the Square D "HOMeline" breakers space out-of-place because Square D says so: You room using this breaker in contradiction to its labeling and also instructions, i beg your pardon violates NEC 110.3(B).
It also violates NEC 110.2, which needs all devices must be approved.
Siemens does do classified breakers. They do the QD kind for Square D "QO" panels, and also the MSQ kind also for Square D "QO" panels. Now, Siemens" website just shed down therefore Google is useless (every web page is 404). But from Google"s view of your pages, it"s clear they don"t do UL-classified breakers because that GE panels. Also if castle did, their MP-T form is not that; being made specifically for Murray lineage panels. As such, 110.3(B) and 110.2 apply, exact same as above.
The ideal GE breakers space perfectly fairly priced.
See more: 14 Is 28 Percent Of What Number, Solved: = 50
If castle weren"t (QO isn"t), then you could think about classified breakers made for that panel, such as Eaton CL. Carry out not usage Eaton BR; as discussed earlier, a manufacturer"s classified lines are incompatible with their very own panels, uneven they are additionally classified for their own panels (The reality Eaton didn"t classify the CL line for BR probably means they can"t.)